Buy Analogue input module,IE8 mA IE8. Browse our Mfr. Part No. IE8; Brand Allen Bradley I/O,module,Flex User Manual. Legislation. (Cat. No. IE8 Series B). 4. 1. 3. 2. 5. 6. 7. Module Installation. This module mounts on a terminal base unit. 1. the module. Installation Instructions. User manual • Read online or download PDF • Rockwell Automation IE4XOE2,IE8,OE4,D FLEX I/O ANALOG MODULE User.
|Published (Last):||26 January 2007|
|PDF File Size:||9.60 Mb|
|ePub File Size:||8.98 Mb|
|Price:||Free* [*Free Regsitration Required]|
Adapter Input Status Word. For example, for the 8 input analog module, you have 9 input words, and 6 output mwnual. Block transfer read BTR programming moves status and data from the module to the processor’s data table. The following chart lists each chapter with its corresponding title and a brief overview of the topics covered in that chapter.
IE8 & OE4 User Manual_百度文库
The module is configured using a group of data table words that are transferred to the module using a block transfer write instruction. Connecting Wiring for the Analog Modules. This allows you to define a safe operating state for controlled devices which depend on the analog output from the module.
This bit is set to 1 when all bits in the configuration register write word 3 are 0 unconfigured state. Press the terminal base down onto the DIN manuxl until flush. Reading Data From Your Module Read programming moves status and data from the module to the processor’s data table. Refer to range selection above. If interlocks are removed, 1749-ie8 program may not work properly.
Scripting must be enabled to use this site.
The two’s complement of 0 then is still 0. Data Format The data returned from the analog-to-digital converter in the module is bit resolute. If the adapter does not establish communication with the module, cycle power to the adapter. Channel 1 analog data – 12 bit left justified two’s complement number; unused lower bits are zero; 4 20mA manua, all 16 bits.
This bit is set 1 when an error is detected in slot position 6. If the adapter does not recognize your module after installation is completed, cycle power to the adapter. The second compute instruction has a final destination of an integer location. Channel 2 Safe State analog value – 12 bit left justified two’s complement number; unused lower bits are zero; 4 20mA uses all 16 bits. An electrical arc can cause personal injury or property damage by: When set 1indicates either a broken or open input wire, or input current is at or below 4mA.
Configure select bits C for individual channels – Bit 08 corresponds to input channel 0, bit 09 corresponds to input channel 1, and so on. Thereafter, the program continuously performs read block transfers to configure the module. When you remove or insert a module with field-side power applied, an electrical arc may occur.
Full range bits F for individual channels – Bit 00 corresponds to input channel 0, bit 01 corresponds to input channel 1, bit 02 corresponds to input channel 3, bit 03 corresponds to input channel 3, bit 04 corresponds to output channel 1, and bit 05 corresponds to output channel 2.
Analog modules have 15 words assigned to them. If you do not, refer to the appropriate programming and operations manual before you attempt to program your modules. Use caution to make sure that the female flexbus connector does not strike any of the pins in the mating male connector.
Repeat for each remaining terminal base unit. Throughout this manual we make notes to alert you to possible injury to people or damage to equipment under specific circumstances. Repeat the above steps to install the next module in its terminal base unit. PLC-5 — determine a constant slope by dividing the desired range by the actual range. Not used – set to 0 Power Up bit – included in series B modules only.
Channel 7 analog data sign bit. The module is seated when the latching mechanism 7 is locked into the module.
Rockwell Automation 1794-IE4XOE2,1794-IE8,1794-OE4,D17946.5.2 FLEX I/O ANALOG MODULE User Manual
The processor’s user program initiates the request to transfer data from the input module to the processor. Channel 1 analog data sign bit. Channel 5 analog data sign bit. Channel 3 analog data – 12 bit left justified two’s complement number; unused lower bits are zero; 4 20mA uses all 16 bits. Mnaual the result by your data, and add or subtract any offset.
Secure to the wall with two 6 self-tapping screws. On Series modules, 2V or 4mA is output until the janual is configured. You can reduce the input words to 8 by not using the underrange settings set in word 9.
Channel 1 Safe State analog value – 12 bit left justified two’s complement number; unused lower bits are zero; 4 20mA uses all 16 bits. Your program should monitor status bits, block transfer read and block transfer write activity.
Separate power connections may be necessary.